Check up to five results to perform an action.
These cables are specifically approved for power, control, lighting and signal circuits, in manufacturing, industrial and commercial installations. For use in direct burial, in cable trays, in raceways, or where supported in outdoor locations by a messenger wire.
In cable tray in hazardous (classified) locations Class I, Division 2 per NEC, also as Class I circuits per Article 725, and in Class II, Division 2, as permitted per NEC. When installed in accordance with NEC 336.10(7), TC-ER marked cable is approved for use as open wiring between a cable tray and the utilization equipment or device.
Assembly consisting of three or four insulated aluminum alloy AA8000 compact stranded conductors, cabled together with a bare equipment grounding conductor and non-hygroscopic fillers. The sub-assembly is wrapped with binding tape and a PVC jacket is applied over the taped assembly. PVC jacket is sunlight resistant, moisture resistant and flame retardant. This cable uses XHHW-2 conductors that are phase identified, including one insulated black conductor, one insulated white conductor, and one insulated conductor with a single longitudinal red stripe. If required, a fourth insulated conductor has a single longitudinal blue stripe. Phase conductors are insulated with cross-linked polyethylene (XLPE) and rated for a maximum operating temperature of 90° C in dry and wet locations, rated for 600 volts maximum operating voltage. Insulation is free of harmful heavy metals in compliance with RoHS, Directive 2002/95/EC.