Check up to five results to perform an action.
The insulation shall be a premium quality, heat, moisture, ozone and corona resistant thermosetting ethylene propylene; TYPE I, II or III as listed in ICEA S-93-639 or ICEA S-97-682. The cable manufacturer shall compound the insulation material with in its own or remotely owned facilities. The insulation shall be compatible with both the conductor shield and the insulation shield. The thickness shall be at the 100% or 133% level as applicable and in accordance with the latest edition of ICEA.
S-93-639, ICEA S-97-682 and UL 1072. The diameters over the insulation shall be in accordance with ICEA S-97-682. The EPR insulation shall also meet the guaranteed values as listed in the table below.