Applications As flame-retardant three-conductor power cables rated 600 volts, 90 Deg. C. in dry locations. 75 Deg. C. in wet locations. Specifically approved for installation in cable trays per Article 336 of the NEC. Type TC cable is also approved for use in Class I and II, Division 2 hazardous locations. Cables may be installed in open air, in ducts or conduits, in tray or trough, or direct buried.
Construction Individual conductors of stranded uncoated copper Type THWN or THHN, surface print phase identification. Three insulated conductors twisted with a Class B stranded uncoated copper grounding conductor and fillers, cable tape, PVC jacket overall, surface printed.
Listed by UL as Type TC Tray Cable per Article 336 of the NEC.
Individual conductors UL listed as Type THWN or THHN.
Overall jacket UL listed as Sunlight Resistant.
Cables UL listed for Direct Burial.
Cables UL listed for Open Wiring.
Cables pass UL and IEEE-383 ribbon burner tests and ICEA 210.00 BTU/hour test.
AMPACITY in accordance with the National Electric Code for cables in uncovered cable tray without maintained space and for cable in raceway or direct buried. 90 ºC conductor temperature for dry locations, 75 ºC conductor temperature for wet locations, 30 ºC ambient temperature.
Grounding conductor per UL Standard 1277 for Type TC Tray Cable.