Applications As flame-retardant multi-conductor control, signal or power cables rated 600 volts, 90 Deg. C. in dry locations, 75 Deg. C. in wet locations. Specifically approved for installation in cable trays per Article 336 of the NEC. Also approved for use in Class 1 remote-control and signaling circuits per Article 725 of the NEC. Type TC cable is suitable for use in Class I and II, Division 2 hazardous locations. Cables may be installed in air, in ducts or conduits, in tray or trough, and are suitable for direct burial.
Construction Individual conductors of stranded uncoated copper Type TFN (16AWG). Type THWN or THHN (14-10 AWG), color coded, two conductors flat, three or more conductors twisted, PVC jacket overall, surface printed.
Listed by UL as Type TC Tray Cable per Article 336 of the NEC.
Individual conductors UL listed as Type THWN or THHN (14-10 AWG) or Type TFN (16 AWG).
Overall jacket UL listed as Sunlight Resistant.
Cables UL listed for Direct Burial.
Cables with grounding conductor UL listed for Open Wiring.
Cables pass UL and IEEE-383 ribbon burner tests and ICEA 210.00 BTU/hour test.
Cables designated (w/g) contain an additional bare copper grounding conductor, same size as circuit conductors, and are UL listed for Open Wiring.
Standard color coding is ICEA Method E2 or K2 for NEC applications. This color coding method omits white and green from the color sequence.
ICEA Method 4 color coding is also provided. This consists of printed numbers and words, 1-ONE, 2-TWO, etc.