Used for primary and secondary overhead distribution where limited space is available or desirable for rights of way. Installed as an uninsulated conductor; however, covering is effective in preventing direct shorts and instantaneous flashovers should tree limbs or other objects contact conductors in such close proximity. The resulting close-proximity configuration minimizes the amount of space and hardware required for line installation; particularly useful in congested areas such as alleyways or tight corridors.
Conductors are concentric strand AAC (1350-H19), AAAC (either compressed or full compact depending on conductor size) or ACSR. The conductor shield shall be an extruded back semiconductor polymer meeting the physical requirements of ICEA S-61-402. Available with track-resistant high-density polyethylene (TR-HDPE) per ASTM D1248 or Track-Resistant Cross-linked Polyethylene (TK_XLPE) covering per ASTM D2656 and ICEA S-66-524. The minimum thickness of each layer at any point shall not be less than listed in the data table. The outer layer shall contain a carbon black additive, not less than 0.02% to provide the weather resistance, and track resistance.
15kV - 35kV Covered Aerial Medium Voltage Cable wire meets or exceeds all applicable ICEA specifications and the following ASTM specifications: